EC29 or Error Code 29
A 29 error code indicates a neutralizer2 drainage failure. The neutralizer2 is designed to drain condensate1 away from the heater. If the neutralizer2 and/or drain becomes blocked up, the unit will flash the 29 error code to prevent the burner from being flooded.
Common issues related to the 29 error code include:
- Blockage in the condensate1 drain line
- Incorrect condensate1 line piping (e.g. upward sloping of drain line, trapped drain line, incorrect size piping)
- For NRCP or CB models: Restriction or obstruction in the intake or exhaust venting.
Local Service Representatives can be found at http://support.noritz.com/servicereplocator.php
Liquid water that forms when the water vapor, developed as a product of combustion, contained in exhaust gases cools enough to change into a liquid.
A device used to raise the pH of acidic condensate to a value close to 7 (neutral).
- Models: All high efficiency condensing unit that utilize PVC, CPVC or PP venting.